CL series of 2V VRLA batteries are recognized as the most reliable and high quality battery system in the industry. They are designed with advanced AGM(Absorbent Glass Mat) technology, Long service life designed with 10-12 years, the batteries comply to the most popular international standards, such as IEC60896-21/22, BS6290-4, Eurobat Guide.
1. Environmentally friendly
2. Completely Maintenance-Free
3. Non-Spillable construction design.
4. Wide OperatingTemperatureRange(-20~+60)
5. Longer Life(10-12years designed life)
6. Explosion Proof
7. Valve Regulated & High Discharge Rate Capability
8. Low Self Discharge
9. Independent of Position
10. Ease of Shipment
11. No need of balanced charge or boost
12. No Memory
Communication equipment, Telecommunication control equipment; Emergency lighting systems; Electric power systems; Power station; Nuclear power station; Solar powered and wind powered systems; Load leveling and storage equipment; Marine equipment; Power generation plants; Alarm systems; Uninterruptible power supplies and stand-by power for computers; Medical equipment; Fire and security systems; Control equipment; Stand-by electric power.
Operation and maintenance manual
For maintenance free battery, it's free maintenance in the operation. But we can only use it in proper operation to keep the long lifetime of the battery,
(1) Battery Installation
Batteries should be installed possibly in a clean, cool, ventilated and dry place. The battery should be placed upright. Each terminal between the batteries is connected firmly.
(2) The ambient temperature
Ambient temperature is important factor for the battery operation. When the ambient temperature is too high, Battery plate corrosion will be increased, while absorbing more moisture; When the ambient temperature is too low, the battery will not be full charged. All this will affect the battery life. Therefore we suggest the working ambient temperature is around 25.
(3) The charge and discharge current
Battery charge and discharge current usually uses the concept C, the actual value of C is related to the capacity of the battery. For example, a 100AH battery: 1C = 100A. Charging current is around 0.1C; The charging current must not be bigger than 0.3C. Discharge current general requirements in 0.05 ~ 3C range.
(4) Charging voltage
After the battery is full converted to float charging, the float voltage is around 13.0V. If the charging voltage is too high will cause the battery overcharge, otherwise the battery will not be full charged. Charging voltage is abnormal, it may be caused by the battery configuration error, or it may be caused by controller failure. Do not choose the controller with bad quality.
(5) The depth of discharge
Depth of discharge of the battery life is also a important factor for lifetime of battery, the deeper the battery discharge, the fewer the number of cycles, so battery should avoided from deep discharge.
(6) Regular maintenance
Battery should be regular checked in every period time after used, such as check its outlook, measuring the average voltage of each battery, etc.
1. High efficiency Discharge: Sealed reaction efficiency rate more than 99.9%
2. Low rate of liquid loss: Liquid loss rate is half lower than adsorbed type battery. Effectively alleviate the electrolyte early dry.
3. Low Self discharge: Storage with power for two years among temperature 25 is possible. Storage time is 4times longer than adsorbed type battery.
|Rated Capacity(AH) 10hrs/25ºC||Approx. Weight||Dimensions(mm)||Terminal Type|
Deep Cycle AGM Battery
Maintenance Free Battery
Sealed Lead Acid Battery
Lead Acid Battery battery